The site for free, objective information you can use!
Search the site
Home - Who are we? - Government Hotlines - How to get help - FAQs - Quick links: Today's Federal Register - Contact Info for: EPA - State agencies - OSHA - DOT Regs: Search Government regs and sites Data: Search EPA databases
There are four general classifications of fires and extinguishing agents:
Class A fires are those that involve ordinary combustible materials such as wood, paper, cloth, rubber and plastics. The quenching and cooling effects of water or of solutions containing large amounts of water are the most effective means of extinguishing this type of fire.
Class B fires are those that occur in the vapor-air mixture over the surface of flammable liquids such as gasoline, oil, grease, paints and thinners. The limiting of air (oxygen) or the combustion inhibiting effect is the most effective measure against incipient fires of this class. Water must not be used on Class B fires because it tends to spread the fire.
Class C fires are those that occur in or near energized electrical equipment where non-conducting extinguishing agents must be used. Water must never be used on Class C fires.
Class D fires are those that involve combustible metals such as magnesium, titanium, zirconium and sodium. Water must never be used on class D fires. A Class D powdered extinguishing agent should be used.
|Light(Low)Hazard Occupancy||Ordinary(Moderate)Hazard Occupancy||Extra(High)Hazard Occupancy|
|Minimum rated single extinguisher||2-A||2-A||4-A*|
|Maximum floor area per unit of A||3,000 sq ft**||1,500 sq ft.||1,000 sq ft.|
|Maximum floor area for extinguisher||11,250 sq ft**||11,250 sq ft**||11,250 sq ft**|
|Maximum travel distance to extinguisher||75 ft.||75 ft.||75 ft.|
* Two 2 1/2 gallon (9.46 L) water type extinguishers can be used to fulfill the requirements of one 4-A rated extinguisher.
** See pamphlet 10, Portable Fire Extinguishers, National Fire Protection Association, 1981 Edition.
|Type of Hazard (m 2 )||Basic Minimum Extinguisher Rating||Maximum Travel Distance to Extinguishers (ft.)|
Extinguishers with Class C rating shall be required where energized electrical equipment may be encountered which would require a non-conducting extinguishing medium. This will include fire either directly involving or surrounding electrical equipment. Since the fire itself is a Class A or Class B hazard, the extinguishers are sized and located on the basis of the anticipated Class A or B hazard.
This page was updated on